Связться с нами: +380503524688 | +380505369255 email@example.com
Service of stations of biological cleaning of drains Topas
Installation maintenance is simple and does not need specially trained personnel. The biological wastewater treatment plant TOPAS Automatic is equipped with an electronic unit, which at the time of switching on the power supply will measure the level in the receiving chamber, the SBR reactor and independently switch on the necessary mode of operation. The biological wastewater treatment plant TOPAS Automatic is equipped with an electronic unit, which at the time of switching on the power supply will measure the level in the receiving chamber, the SBR reactor and independently switch on the necessary mode of operation.
When designing the station, we assume that the user himself would be able to carry out independently maintenance:
Visual inspection of purified water;
remove waste sludge from the sump using a pump once a quarter, or every six months, depending on the accumulation of sludge in the sludge collector;
untimely pumping of surpluses of activated sludge leads to thickening of it and subsequently to disruption of the operation of the installation;
replacement of compressor membranes once every 2-3 years (it depends on the configuration);
clean the collection device for non-recyclable particles 3-4 times a year;
remove and clean the filter of large fractions 1 time in 3 months;
replace aeration elements once in 10-12 years;
If necessary, our service department will carry out all these, you only need to conclude a service contract. When installing a sewage treatment plant with a GSM module, the company will provide comfort comparable to connecting to the urban sewage system, while you will still have the opportunity to use industrial water for watering. We recommend that you familiarize with the model range of Topas Automatic stations.
Discharge into the sewage of construction debris (sand, lime, etc.), this leads to clogging of the installation and as a consequence a loss efficiency
Discharge the polymer films and other biodegradable compounds into the sewage system (this category includes condoms, hygiene bags, cigarette filters, films from cigarette packs, etc.), it can block the and, as a result, the installation is not functioning;
Discharge rinse waters from pool filters;
Discharge medicines and drugs into the sewage system;
Discharge into the sewage system of engine oils, antifreeze, acids, alkalis, alcohol, etc.
Dumping a large amount of pet hair.
Discharge of toilet paper into the sewer;
Discharge of drains of washing machines into the sewage system;
Discharge into the sewage of kitchen drains;
Discharge into the sewer of shower and bath drains.
Using of household chemicals at home does not affect the operation of the sewage treatment plant. Aeration removes the Chlorine contained in disinfectants. For life of biomass, PH-reducing agents are dangerous but not chlorine containing.